Down to Earth Construction Services have a septic repair appointment today in Acushnet MA. Unfortunately when the property owner noticed a wet patch in their yard they added more soil to the patch in the hope that this would fix the problem. This fix only temporarily covered up their septic problem and the wet patch returned and they contacted us when they also noticed a pronounced sewage odor in the area. We were able to determine that a new gutter in addition to a newly paved driveway was resulting in additional water being diverted to the soil absorption field area which put an extra load on the system. When their soil was saturated with clean water, even seasonally, it could not accept any more wastewater. The untreated wastewater was therefore rising to the surface. We were able to improve surface and subsurface drainage by diverting all surface and groundwater away from the soil absorption field. The soil could absorb all the wastewater from the property. We have other septic repair appointments today in Rochester, Freetown, Taunton, Norton, Dighton and Lakeville MA. If you suspect you require a septic repair or if you have any questions about your septic system please do contact our Norton office on 508-622-5759 or visit http://downtoearthconst.com/septic-services/
Down to Earth Construction Services were approached by a property owner in Norton, MA who needed a solution for their failing leach field. We will restore the function of their leach field or drain field with the White Knight system.
In nature, oxygen-using (aerobic) bacteria in the soil consume non-living organic material. This is the process nature uses to “recycle” wastes. We install the White Knight™ Microbial Inoculator/Generator in the septic tank to create an oxygen rich environment and cultivate an extensive colony of these same soil bacteria.
The result is nearly complete consumption of the organic materials entering the septic tank. At the same time, the bacteria are carried into the leach field where they consume the organic material that has accumulated in the underlying soil. The leach field regains and/or maintains its capacity to deliver effluent to the soil for purification.
The White Knight™ advantage includes:
- An installation costs thousands of dollars less than that of a replacement leach field
- Minimal disruption to existing landscape
- Protection of the environment
- Significantly longer tank pumping interval
- Conservation of natural resources
- 100% component and limited lifetime performance warranty
We have successfully used this system throughout the region to restore leach fields from Wayland to Upton to Fairhaven and Marshfield MA.
The White Knight™ Microbial Inoculator/Generator can be used to:
- Improve the function of a marginally operating drain field
- Restore the function of a totally failing leach field
- Improve the quality of effluent returning to the soil and ground water
- Reduce the amount of nitrate moving into the environment
- Reduce the size of a leach field required for new building construction
- Expand the size of existing structures without expanding the leach field
If you want to have a White Knight Septic Installation or have questions please do contact our Norton, MA office on 508-622-5759 or visit Down to Earth Construction Services
Down to Earth Construction Services understand the entire septic system and all of its components to enable us to provide the best septic services possible to our clients. Today we are replacing a baffle, installing an outlet tee and replacing a d-box for a customer in Attleboro MA. We have other septic repair appointments scheduled today in Norton, Rehoboth, Taunton, Raynham, Dighton and Berkley MA. When we are contacted by a customer because they believe they need a septic repair we will assess the condition of their septic system and then present them with a range of options designed to correct any identified issues. These may include one or more of the following:
- Replacement of damaged or missing baffle
- Installation of effluent filter and service riser
- Installation of pumping access riser and cover
- Installation of curtain drains
- Replacement of deteriorated components
- Repair or replacement of damaged components
- Removal of accumulated solids in leach field piping
- Removal of plant and tree roots in leach field piping
- Installation and service of the White Knight™ Microbial Inoculator/Generator
- Diversion of water softener/conditioner backwash discharges
- Detailed explanation of our Septic Use Guidelines
If you require a septic repair or if you have septic concerns or questions about your septic system please do contact our Norton office on 508-622-5759 or visit Down to Earth Construction Services
Down to Earth Construction Services has extensive experience installing entirely new septic systems and upgrading existing septic systems. We are also regularly required to repair or replace components of existing septic systems to enable them to keep working, correctly, for many more years. Today we are replacing a D-Box for a customer in Attleboro MA. The septic system D-Box or distribution box is just what its name implies. It distributes wastewater that exits the septic tank into the leach field or drain field. A properly functioning D-Box will do this evenily so the entire field is used and does not get clogged due to uneven distribution. We have other septic repairs today, which include the repair of a septic pump, in Norton, Freetown, Taunton, Rehoboth and Rochester MA. If you require a septic repair or septic upgrade or installation please do contact our Norton Office where were will be happy to answer any questions that you have on 508-622-5759 or visit Down To Earth Construction Services
Down to Earth Construction Services have been contacted by a client in Sharon MA who suspects that they have a leach field problem so they require a septic repair. They have noticed a sewage smell in their yard around the leach field area and there is a consistent wet, sogginess on the field. Other signs that you may have a problem can include lush vegetation over the leach field, frequent pumping of the tank being required, and/or slow drains.
Leach fields fail for two primary reasons. The main reason is referred to as biological clogging. This is the development of a biomat beneath the leachfield that eventually prevents the liquid or effluent from entering the underlying soil. This biomat is a combination of fine organic solids that have been carried out of the septic tank and the remnants of anaerobic bacteria. These bacteria originate in the human intestinal tract and enter the septic system with the waste products. 95% of all leach field failures are biological. The second primary reason is referred to as a mechanical failure. This could be a structural collapse of the leach field piping or chambers, root intrusion, or fine non-organic materials that are washed down to the bottom of the leach field and seal the soil.
Down to Earth Construction Services have many years experience identifying and repairing leach field problems and will find locate and solve our client’s leach field problem. We have other septic repair appointments today in Dighton, Raynham, Rehoboth and Lakeville MA. If you suspect that you have a septic problem or if you have questions about your septic system please do contact our Norton office on 508-622-5759 or visit www.downtoearthconst.com
Down to Earth Construction Services have experience with all parts of your septic system including the septic tank, leach field or drain field, septic pumps and the D-Box. Today we are replacing a D-Box for a customer in Rochester MA. The distribution box or D-Box must be installed correctly or it will not function properly. We have extensive experience installing, replacing and repairing d-boxes so you can be sure that the work will be done quickly, correctly and with as little disruption as possible. This is always important but especially for our commercial customers for whom delays or problems will cause lost earnings. We also have other septic repairs scheduled today in Carver, Middleboro, Freetown Berkley and Norton MA. If you require a septic repair or if you have any questions about your septic system, whether it supports a commercial property or a residential home please do contact our Norton office on 508-622-5759 or visit the Down to Earth Construction Services website.
Down to Earth Construction Services have a septic repair scheduled today for a customer in Rochester MA. Our client unknowingly planted trees in close proximity to their septic tank and leach field a number of years ago. As the trees have matured and their root systems have extended they have caused damage to the leach field and septic tank of their septic system. We are providing extensive septic repairs which include repairs and replacement of piping and the tank. It is always a good idea to simply have grass covering your septic leach field because large plants, trees and bushes can cause septic problems as we have seen today. We have additional septic repairs scheduled in Freetown, Marion, Mattapoisett, Fairhaven and Fall River. If you need a septic repair or if you have any questions please do contact our Norton office on 508-622-5759 or visit www.downtoearthconst.com
Down to Earth Construction Services can provide our customers with septic system repairs on all parts of their system. Today we are replacing a d-box for a customer in Sharon MA. A septic distribution box (D-Box) is a container used to receive septic system effluent from a septic tank and to re-distribute the effluent into a network of attached drain field or leach field absorption trenches and pipes. The D-box works by gravity, flowing effluent into the drainfield (or leach field) piping network. It must be installed correctly to ensure that it distributes evenly. We are also assisting our customer with locating their leach field for easement and have the appropriate permission from their neighbour to do so. This may seem unnecessary but if a homeowner has moved into a property but was not provided with property designs or as built drawings for their property they may be unaware of the location of their septic system components. If your septic system is working correctly there should be very little evidence of the location of a leach field. However we have extensive experience with septic systems so will be able to locate a leach field when a homeowner may not be able to do so. We also have additional septic system repairs scheduled today in Mansfield, Norton, Taunton, Canton and Foxboro MA. If you require septic system repairs or if you have any questions about septic systems please do contact our Norton office on 508-622-5759 or visit http://www.downtoearthconst.com
Down to Earth Construction Services has septic repairs scheduled today including a sewage pump repair and leach field repairs in Fall River, New Bedford, Seekonk, Swansea, Westport, Marion and Mattapoisett MA. We strive to provide our customers with professional, thorough, environmentally responsible and cost effective solutions to their septic problems. If you require septic repairs or if you have questions about your septic system please do contact our Norton office on 508-622-5759 or visit www.downtoearthconst.com
Down to Earth Construction Services know that in the beautiful New England Summer many people are out in their yards planting and gardening. Unfortunately when you are planting large shrubs or trees in your yard if you do so on your leach field you can unknowingly create a septic problem. The roots and sometimes weight of plants can actually damage your drain field which means that your septic system is no longer working correctly. Septic systems do an amazing job of returning liquids to the soil for purification but the whole system needs to be functioning correctly for this to happen. When septic system failure occurs, the conditions they create are dangerous. These can include:
Hazardous sewage surfacing in yard
Health hazards to children and pets
Noxious odors over large areas
Polluted streams and ponds
Sewage back-up in buildings
Breeding areas for mosquitoes
Today we are at a customer’s home in Rochester, MA repairing their leach field which has been damaged when they planed an orchard over it last year. The roots combined with heavy machinery being parked on the drainfield during construction have both lead to the structural collapse of the leach field piping. A strong sewage odor and dampness over their yard was luckily a sign of a septic problem that the homeowners did not ignore. We can repair the damage so they do not have to worry about the consequences of an inoperative septic system. We also have other septic repairs scheduled today in Rochester, Seekonk, Fairhaven, Fall River and Mattapoisett MA. If you require a septic repair or if you have any questions about septic systems please do call us at our Norton office on 508-622-5759 or visit www.downtoearthconst.com