Down to Earth Construction Services have a septic repair appointment today in Acushnet MA. Unfortunately when the property owner noticed a wet patch in their yard they added more soil to the patch in the hope that this would fix the problem. This fix only temporarily covered up their septic problem and the wet patch returned and they contacted us when they also noticed a pronounced sewage odor in the area. We were able to determine that a new gutter in addition to a newly paved driveway was resulting in additional water being diverted to the soil absorption field area which put an extra load on the system. When their soil was saturated with clean water, even seasonally, it could not accept any more wastewater. The untreated wastewater was therefore rising to the surface. We were able to improve surface and subsurface drainage by diverting all surface and groundwater away from the soil absorption field. The soil could absorb all the wastewater from the property. We have other septic repair appointments today in Rochester, Freetown, Taunton, Norton, Dighton and Lakeville MA. If you suspect you require a septic repair or if you have any questions about your septic system please do contact our Norton office on 508-622-5759 or visit http://downtoearthconst.com/septic-services/
Down to Earth Construction Services are continuing work on a septic installation starting today in Uxbridge, MA. This installation is for a customer who had a failed septic system and through consultation we designed a new septic system for them which would be more cost effective, environmentally sound and efficient than their old septic system. We will always find the best solution for our customers with failing septic systems which can include septic system rejuvenation, septic system repair or an entirely new septic installation. Our septic designs and septic system installations are entirely tailored to our clients’ requirements so we know that they will be satisfied with the results that we can provide. We have recently installed septic systems for customers in Sharon, Fall River and Acushnet MA. If you have have a failing septic system or are interested in having a septic installation please do contact our Norton, MA office on 508-622-5759 or visit http://downtoearthconst.com/septic-services/ for more information or to answer any questions that you have.
Down to Earth Construction Services know that septic systems have to be used correctly for them to continue to work efficiently and function as they should. A large part of this is is just knowing what is being introduced to your septic system and making sure that anything that goes into it is appropriate and wont adversely affect your system. All wastewater makes its way to your septic system and everything that goes into your sink, toilet, washing machine and shower/bath will also get introduced into your septic system. Keep the following items out of your septic system to prevent problems:
cooking oils or grease
feminine hygiene products
any/all latex products
hazardous chemicals, pesticides and latex-based paints
water purification back flush
It is important to note, however, that each system is unique. Check with your septic system installer or manufacturer for a complete list of items that should not make their way into your system for maximum efficiency. There are also many other things that should stay out of your system and there is no way that we can list all of the items. We have found toys, dead fish, clothing and jewellery in septic systems and all of these items were causing a problem that led to us investigating the cause. Simply put if you are not sure do not put it in your wastewater. We have septic repairs scheduled today in Carver, Middleboro, Marshfield, Marion and Rochester MA. One of these repairs is necessary because the homeowner was unaware of the large volume of sand that was being introduced to their septic system via the washing machine and shower by their teenage children. It is wise to make sure that your entire family and visitors know that you have a septic system and there are certain, easily followed guidelines to follow to make sure you do not require a septic repair from our talented technicians. If however you do suspect that you require a septic repair or if you have any questions about septic systems please do contact our Norton office on 508-622-5759 or visit Down to Earth Construction Services
Down to Earth Construction Services understand the entire septic system and all of its components to enable us to provide the best septic services possible to our clients. Today we are replacing a baffle, installing an outlet tee and replacing a d-box for a customer in Attleboro MA. We have other septic repair appointments scheduled today in Norton, Rehoboth, Taunton, Raynham, Dighton and Berkley MA. When we are contacted by a customer because they believe they need a septic repair we will assess the condition of their septic system and then present them with a range of options designed to correct any identified issues. These may include one or more of the following:
- Replacement of damaged or missing baffle
- Installation of effluent filter and service riser
- Installation of pumping access riser and cover
- Installation of curtain drains
- Replacement of deteriorated components
- Repair or replacement of damaged components
- Removal of accumulated solids in leach field piping
- Removal of plant and tree roots in leach field piping
- Installation and service of the White Knight™ Microbial Inoculator/Generator
- Diversion of water softener/conditioner backwash discharges
- Detailed explanation of our Septic Use Guidelines
If you require a septic repair or if you have septic concerns or questions about your septic system please do contact our Norton office on 508-622-5759 or visit Down to Earth Construction Services
Down to Earth Construction Services regularly provide septic system installations and septic repairs for customers throughout the region. We have all of the equipment required for the excavation, installation and landscaping of a new septic system or large septic repair or replacement. We also, however, regularly provide other septic services including septic system inspections to customers who have a septic system and need an inspection. In Massachusetts a system inspection is required in the following instances:
- Within 2 years before a sale. If weather conditions prevent inspection at the time of a sale, the inspection must take place within 6 months afterward.
- When there is a proposed change to the facility which requires a building or occupancy permit.
- Any change in the footprint of a building, to make sure that new building construction will not take place on top of any system components or on the system’s reserve area.
- For large systems with a design flow of 10,000 to 15,000 gallons per day or more at full build-out, on the basin schedule shown in 310 CMR 15.301(6), and every five years thereafter.
- Every 3 years for shared systems.
- When the property is divided, or ownership of 2 or more properties is combined.
- When MassDEP or the local Board of Health orders an inspection.
For more information see the Mass Gov Website.
Today we have septic system inspections scheduled in Wrentham, North Attleboro, Plainville, Blackstone, Bellingham and Franklin MA. If you require a septic inspection for your septic system or if you have any questions about septic systems please do not hesitate to contact us at our Norton office on 508-622-5759 or visit Down to Earth Construction Services
Down to Earth Construction Services have been contacted by a a property owner in Middleboro MA who needs a septic repair which entails having their septic tank baffles replaced. Broken septic tank baffles result from sulfuric acid eating away at concrete baffles or rust eating away at steel baffles. A septic tank has an inlet and outlet baffle. Usually these baffles are made from concrete and are part of the tank construction. The inlet baffle slows the flow of liquid entering the tank and decreases the turbulence allowing the solids to settle in the bottom of the tank. The outlet baffle helps to retain the solids and prevent them from leaving the tank and travelling to your drain field. A tank without an outlet baffle can compromise the longevity of your septic system and cause premature failure. We are experienced working with all parts and types of septic system so can quickly and with minimum disruption replace our client’s damaged baffles. We also have other septic repair appointments scheduled today in Carver, Bridgewater, Taunton, Raynham and Norton MA. If you require a septic repair or have questions about your septic system please do contact our Norton office on 508-622-5759 or visit Down to Earth Construction Services
Down to Earth Construction Services regularly carry out septic repairs and septic maintenance for customers on all types and parts of septic systems. Today we have pressure distribution maintenance, repairing laterals under the pavement and installing a filter for a customer in Rochester, MA. Septic tanks and drain fields have been used for many years but not all soil and site conditions work well for gravity septic systems. The pressure distribution system is one alternative that provides dosing and resting cycle, a uniform distribution of wastewater and shallow placement of the drainfield. Installing a filter from your wastewater into the septic tank will help to keep solids from clogging the pump and drainfield pipes. We also have other septic repairs and some septic maintenance scheduled today in Seekonk, Swansea, Freetown and Norton MA. If you require a septic repair or have questions about your septic system please do contact our office on 508-622-5759 or visit www.downtoearthconst.com
Down to Earth Construction Services know that spending money on your septic system, especially when Thanksgiving and Christmas are coming up quicker than you’d think does not always seem to be a priority. Home maintenance, like septic repairs, is not a fun way to spend our hard earned money especially when it is not seen or enjoyed. However if you have a concern about your septic system it is wise to have it addressed immediately and not leave it until the holidays have passed and you want to be ‘bothered’ by it. Indicators that you may have a septic problem include:
Pipe Gurgling Sounds
Toilet Flushing Issues
Greener Grass on your leach field
Patches of Standing Water
If you have noticed one or more of these signs at your property please do consider calling to discuss your concerns with our experienced technicians. If a septic problem is left it is very unlikely to ‘fix itself’ and could quite possibly become a much larger and more expensive issue to repair. Today we have septic repairs scheduled in North Attleboro, Foxboro, Plainville, Wrentham, Norton and Attleboro MA. If you wish to schedule a septic repair or if you have septic questions or concerns please do contact us at our office on 508-622-5759 or visit Down to Earth Construction Services
Down to Earth Construction Services has extensive experience installing entirely new septic systems and upgrading existing septic systems. We are also regularly required to repair or replace components of existing septic systems to enable them to keep working, correctly, for many more years. Today we are replacing a D-Box for a customer in Attleboro MA. The septic system D-Box or distribution box is just what its name implies. It distributes wastewater that exits the septic tank into the leach field or drain field. A properly functioning D-Box will do this evenily so the entire field is used and does not get clogged due to uneven distribution. We have other septic repairs today, which include the repair of a septic pump, in Norton, Freetown, Taunton, Rehoboth and Rochester MA. If you require a septic repair or septic upgrade or installation please do contact our Norton Office where were will be happy to answer any questions that you have on 508-622-5759 or visit Down To Earth Construction Services
Down to Earth Construction Services have the experience and knowledge to identify and repair septic problems when they arise for our customers. Today we are replacing an outlet baffle for a customer in North Attleboro, MA. The outlet baffle directs the flow of effluent from the tank to the drainfield or leach field; it prevents the scum layer from going straight into the outlet pipe and causing drainfield clogs and premature system failure. Our customer had noticed sewage smells coming from their septic system and chose to contact us to investigate the issue. We were able to determine that the cause was a defective outlet baffle and will be able to replace the baffle and therefore ensure that the smell will disappear but more importantly there won’t be any larger and more serious problems created by this issue. We also have septic repairs including a septic pump repair today in Wrentham, Plainville, Blackstone and Foxboro MA. If you are concerned that you require a septic repair or if you have any questions about your septic system please do contact our Norton Office on 508-622-5759 or visit www.downtoearthconst.com